Top Rated Local AC Repair & Plumbing Services in Conroe, TX
Our family are the professionals to call when it comes to Air Conditioning, Heating & Plumbing service for your homes and businesses in Conroe, TX. Our family gives you our personal promise that we won’t be happy until you’re 100% satisfied! Our reputation is based on your 100% satisfaction, and we take that promise seriously. It’s a part of our company mission!
Zip Codes and Area Served:
Call us now at (936) 271-2030 for fast and friendly service. We’d love the opportunity to earn your business as we have with your Conroe, TX neighbors.
See what your neighbors are saying about our services below!
for Conroe, TX
Our Reviews by City
Roddy - Conroe, TX
very professional awsome job
Billy - Conroe, TX
Juan was very sharp and professional in all points of job
Water pressure issues
James - Conroe, TX
Charles - Conroe, TX
Honest, reliable company.
Shaun - Conroe, TX
Mario was very knowledgeable and explained what he was looking at well. Appreciate his great service!
Greg - Conroe, TX
Kayla - Conroe, TX
The service tech showed excellent customer service as well as manners.
Customer service always keep you updated on tech arrival time.
Juliet - Conroe, TX
Excellent service. Highly recommend
Anna - Conroe, TX
MiguelQuintero - Conroe, TX
This is my first business/service experience with Bradbury Brothers (B.B). I observed the following: (1) I had pleasant phone conversations and written correspondence with Kara, Patty, and Chancy during the process of establishing an appointment. (2) The service technician, Mr. Mario Silva, arrived on time to inspect the two A/C units. He did a thoroughly inspection of the equipment.
Replaced sewer line
Customer had us out today to give estimates to replace two 50 gallon tall NG water heaters. Both heaters are leaking. Gave estimates for 6 year, 10 year and tankless options. Customer will follow up with us if they want the work done.
Set new bathtub faucet, shower faucet and lavatory faucets. Connected all drains and water lines to all. Set new toilet and connected water to it . Turned all water on and checked for leaks . Found none and everything was working with no issues .
CU-3 threw the belts off Troubleshot and found belt on AHU 2 was broken causing the other (2) belts to come loose and fall off. Replaced (1) belt and adjusted motor. Belt was not warranty. All operational upon departure
Came out today because the customer was getting discoloration on the hot side and his water system after turning the softener on bypass. The cold side Had gone clear but the hot side was still black. We ended up doing a good flash on the water heater and it seem to resolve the issue, all the fixtures are running clear now in the house. Customer paid with a credit card no follow-up needed.
Arrived to the Rogers residence to go over barn power and barn build out. Will need some time to put a estimate together. Mr. Rogers asked if we knew somebody that does concrete work and sheet rock work.
Arrived to the Lewis residence to look at a fan that she was having issues with. After looking at the fan I let her know that the fan was bad and she will need to get a new one. I will be sending over an estimate to install the new one that way when she gets it she can reach out to us to schedule it.
Arrive to Mr. Bradyâ€˜s office to look at 4 TVs they would like installed. I have written up the estimate and will email it over. We should do a follow up call on Monday afternoon or Tuesday morning.
Came out today for our annual home inspection. In the kitchen, the garbage disposal sounds as if a bearing is going out. Recommend replacement of the disposal. No other issues were found at this time. Customer is not interested in these recommendations at this time. No follow up.
As Per Agreement
Tub was Backed up in bathroom of left side of house. Had to run hand cable down the line to clear stoppage . Cleared and ran water to test drain. All water took with no issues. Can not warranty stoppages .
System-Main Approx Age of System: 5 Type- R410a Metering Device-TXV SP/HP:136.2/376.4 SLT/LLT:58.7/101.6 VSAT/LSAT-47.4/112.1 Superheat/Subcool-11.4/10.6 Outdoor Entering Air Temp-94.3 Outdoor Fan FLA- R1.2 A1.2 Compressor RLA/LRA- R19.9/109 A13.7/110.8 Contactor Voltage-238/27.1 Capacitor Rating-45/10 A 46.07/8.37 Indoor Return Dry Bulb Temp-74.2 Return Wet Bulb Temp-63.1 Supply Temp- 58 Temperature Difference-16 Required Difference-15-21 Blower FLA- 4.3 Filter Sizes â€“ 16x25x1 16x20x1 Changed Filters â€“ N customer will change Blew out drain line: N Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes-arrived on site met with customer and discussed what they needed with the air conditioner. Found that they wanted an air-conditioning tuneup instead of a diagnostic performed ac tuneup. During tuneup found system was overcharged removed 1 pound of R410a. System is operating within manufacture specifications. Customer had con
Reevaluate water heater replacement as a 3rd water heater was found
Returned ned to install recommendations to all three systems. Installed in line float switches, blow out valves and non ozone air scrubbers. Blew lines out a flushed with a gallon of water each. Systems are operational at the time.
Surveyed job site for upcoming sewer line replacement
AC Diagnostic System: Refrigerant Type R22 Metering Device-TXV SP/HP: 58/236 SLT/LLT: 73/109 VSAT/LSAT: 33/113 SH/SC 40/4 Outdoor Entering Air Temperature 92 Filter Size(s) Returned tstat to original settings: Yes Unit operational; prior to leaving: Yes Found two burned wires on the contactor. Repaired the wiring connectors to get the unit up and running. The condenser fan came on and then after some time the compressor finally kicked on. I found the run capacitor is extremely weak and could fail at any moment. The start capacitor needs to be replaced to make sure the compressor kicks on when itâ€™s supposed to. The unit is still low on refrigerant. This is an indication of a leak within the system. Ms. Masterson is going to talk to her husband this evening on weather they would like to do the repairs and refrigerant and continue to limp this along or go ahead and replace the equipment. Skylar to follow up with Ms. Masterson tomorrow after she talks to her husband this even
System- Approx Age of System: 3yrs Refrigerant Type- R410a Metering Device- TXV SP/HP: 142/296 SLT/LLT: 70/93 VSAT/LSAT- 50/94 Superheat/Subcool-20/1 Outdoor Entering Air Temp- 86 Outdoor Fan FLA- .9 Compressor RLA/LRA- 12.2/157 Contactor Voltage-240/26 Capacitor Rating-38.12/4.99 Indoor Return Dry Bulb Temp- 73 Return Wet Bulb Temp- 60 Supply Temp-60 Temperature Difference- 13 Required Difference- 16-20 Filter Sizes â€“ 25x25x1 Changed Filters â€“ Acceptable Blew out drain line: Y Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes- Unit was operational on arrival. Checked filters. Checked operating pressures and temperatures. Checked indoor and outdoor electrical. Superheat is high and subcooling is low. Temperature split is low. Unit appears to be under charged. Condenser LRA is over rating of 154a. All other components showed no visible issues at this time. Recommend refrigerant and compressor saver-(to reduce amp and exten
Came out today to give a quote for changing out 3 customer supplied toilets. The water heater was temporarily non accessible to look at and not interested in c.c. At the moment but it will be included with the toilet change out should she decide to go with the estimate. She paid the service fee with the 20$ coupon applied. No follow up at the moment.
Homeowner has back today to install parts that were sent by Delta. Did have a problem with getting the water to stop flowing. Finally stopped flow and was able to change out the handles in the cartridges. Tested everything out everything is working properly.
We came out today because the customers home inspector noted lots of concerns about the galvanized piping and needed an estimate to replace these areas. When it comes to galvanized piping it is not recommended to replace small or even large sections in a home like this because once you start cutting into it and making repairs it ends up causing leaks down stream, so we gave estimate to replace the home with or without sheet rock repair. The galvanize definitely needs to be replaced at this point thereâ€™s quite a few areas that are pitting and rusted in the attic visible. The customer is going to relay The information to the realtor and get back with us on a date to come get it done.
System-main Approx Age of System: 2 years Refrigerant Type- R410a Metering Device- TXV SP/HP:136/325 SLT/LLT:59/94 VSAT/LSAT- 47/102 Superheat/Subcool-12/8 Outdoor Entering Air Temp-88 Outdoor Fan FLA- .5 Compressor RLA/LRA-8.6/87 Contactor Voltage-241/25 Capacitor Rating-43/4.6 of 45/5 Indoor Return Dry Bulb Temp-74 Return Wet Bulb Temp-69 Supply Temp- 57 Temperature Difference-17 Required Difference-16-24 Blower FLA- 2.1 Filter Sizes â€“ 20x25x4 Changed Filters â€“ Y truck stock Blew out drain line: N Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes- filter is extremely dirty, recommend replacing to increase efficiency. No other issues found at this time. System is operating and cooling properly. Scheduled next tune up date: Wednesday January 27th 10-2
System- office system Approx Age of System: 12 years Refrigerant Type- R410a Metering Device- TXV SP/HP: 123/318 SLT/LLT: 63/88 VSAT/LSAT-42/100 Superheat/Subcool-21/12 Outdoor Entering Air Temp-90 Outdoor Fan FLA- 0.89 Compressor RLA/LRA-6.51/53.3 Contactor Voltage-212/24 Capacitor Rating- 35.27/5.11 Indoor Return Dry Bulb Temp-70 Return Wet Bulb Temp-59 Supply Temp- 50 Temperature Difference-20 Required Difference-16 Filter Sizes â€“ 20x25x1 Changed Filters â€“ No Blew out drain line: No Returned tstat to original settings: Yes Unit operational; prior to leaving: Yes Notes- Office is cooling properly. Unit is 12 years old and getting toward the end of its life expectancy. System- upstairs apartment Approx Age of System: Refrigerant Type- R410a Metering Device- TXV SP/HP: 129/350 SLT/LLT: 66/101 VSAT/LSAT-44/107 Superheat/Subcool-22/6 Outdoor Entering Air Temp-90 Outdoor Fan FLA- 0.93 Compressor RLA/LRA- 17.15 Contactor Voltage-210/24 Capacito
System-main Approx Age of System: 1 Refrigerant Type- R410a Metering Device- TXV SP/HP:145/322 SLT/LLT:67/99 VSAT/LSAT- 51/100 Superheat/Subcool-25/5 Outdoor Entering Air Temp-88 Outdoor Fan FLA- 1.3 Compressor RLA/LRA-8.6 Contactor Voltage-242/25 Capacitor Rating-67 of 70/5+-6 Indoor Return Dry Bulb Temp-78 Return Wet Bulb Temp-68 Supply Temp-60 Temperature Difference-18 Required Difference-16/24 Blower FLA- 7.5 Filter Sizes â€“ 20x25x1 Changed Filters â€“ N Blew out drain line: Y Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes-Unit is running and operational to manufacturers specs. The unit was installed March 2020. All safety switches are operational, in-line drain is clean and clear. No water in emergency drain pan. Outside unit is working properly and at manufacturers specs. No need for cleaning. Found that the thermostat was malfunctioning and not allowing temp decrease, button does not work. (We did not install new in
As Per Agreement
Repair Follow Up Needed Evaporator coil warranty/repair pricing Downstairs Returned and performed refrigerant leak search. Confirmed leak at evaporator electric sniffer. Added 2lbs of 410a (VSAT/LSAT-51/99 SH/SC-16/6). All authorizations and permissions were given via phone.
System- upstairs Approx Age of System: 8' Refrigerant Type- R410a Metering Device- TXV SP/HP: 138/280 SLT/LLT: 68/92 VSAT/LSAT- 43/98 Superheat/Subcool- 19/1 Outdoor Entering Air Temp- 84 Outdoor Fan FLA- .8 Compressor RLA/LRA-5.9/ 67 of 65 Contactor Voltage-243/26 Capacitor Rating-44 of 45/5 +-6% Indoor Return Dry Bulb Temp-78 Return Wet Bulb Temp-68 Supply Temp- 56 Temperature Difference- Required Difference-16/24 Blower FLA- 3.4 Filter Sizes â€“ 16x25x4 purolator Changed Filters â€“ Y Blew out drain line: N Returned tstat to original settings: Y Unit operational; prior to leaving: Y System- downstairs Approx Age of System: 7 Refrigerant Type- R410a Metering Device- TXV SP/HP: 120/327 SLT/LLT: 60/100 VSAT/LSAT- 42/102 Superheat/Subcool- 18/8 Outdoor Entering Air Temp- 84 Outdoor Fan FLA- .9 Compressor RLA/LRA- 14.55 Contactor Voltage- 240/24 Capacitor Rating- n/a Indoor Return Dry Bulb Temp- 73 Return Wet Bulb Temp- 63 Supply Temp- 53 Temp
As Per Agreement
System- Rudd Approx Age of System: 8 Refrigerant Type- R22 Metering Device- Fixed Orifice SP/HP: 49/234 SLT/LLT: 47/84 VSAT/LSAT- 26/112 Superheat/Subcool-21/27 Outdoor Entering Air Temp- 88 Outdoor Fan FLA- .5 Compressor RLA/LRA- 10.1 Contactor Voltage-242 Capacitor Rating- 50/5 actual Indoor Return Dry Bulb Temp-70 Return Wet Bulb Temp Supply Temp- 49 Temperature Difference-21 Required Difference-15-20 Blower FLA- 3.1 Filter Sizes â€“ 20x25x1 Changed Filters â€“ N clean Blew out drain line: N Customer clears out himself Notes- After 3 pounds SP/HP: 72/222 SLT/LLT: 47/84 VSAT/LSAT- 42/100 Superheat/Subcool- 21/8 Outdoor Entering Air Temp- 88 Customer stated unit was working but it would freeze up sometimes. Checked unit and system is low on refri
Homeowner had us out today due to water pressure issues throughout the whole house. If you have a faucet on and flush a toilet you lose pressure. Found the water softener is not working properly. Bypassed it and everything is working great. Did offer comfort club homeowner is going to talk to his wife and will call if they want to go ahead and do comfort club for everything. He does want an estimate to change out softener to softner. Referred to special work up form.
System- Approx Age of System: 12yrs Refrigerant Type- R22 Metering Device- Fixed Orifice SP/HP: 64/197 SLT/LLT: 48/83 VSAT/LSAT- 37/100 Superheat/Subcool- 10/7 Outdoor Entering Air Temp-88 Outdoor Fan FLA- 1.1 Compressor RLA/LRA- 16.4/157 Contactor Voltage- 240/26 Capacitor Rating-80/10 Indoor Return Dry Bulb Temp-77 Return Wet Bulb Temp- 57 Supply Temp- 59 Temperature Difference- 18 Required Difference- 16-18 Filter Sizes â€“ 2(20x20x1 Changed Filters â€“ Acceptable Blew out drain line: N (No blowout valve) Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes- Unit was operational on arrival. Checked filters. Checked operating pressures and temperatures. Checked indoor and outdoor electrical. Condenser LRA is over rating of 150a. Contactor is humming, pitted and burnt. All other components showed no visible issues at this time. Recommended compressor saver-(to reduce amp and extend equipment life), blowout valve-(to service pri
System-main Approx Age of System: 1 year Refrigerant Type- R410a Metering Device- TXV SP/HP:116/311 SLT/LLT:60/86 VSAT/LSAT- 38/95 Superheat/Subcool-12/9 Outdoor Entering Air Temp-81 Outdoor Fan FLA- .3 Compressor RLA/LRA-14/151 Contactor Voltage-241/26 Capacitor Rating-70/7.4 of 70/7.5 Indoor Return Dry Bulb Temp-69 Return Wet Bulb Temp-63 Supply Temp- 47 Temperature Difference-22 Required Difference-16-24 Blower FLA- 6.4 Filter Sizes â€“ 20x25x1 Changed Filters â€“ N Clean Blew out drain line: N Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes- subtle amount of organic growth spotted in supply plenum, recommended an air scrubber to kill off organic growth, help prevent further buildup, as well as increase air quality. No other issues at this time, coil and condenser were installed last year and system is cooling and operating within manufactured specs. Customer is moving out of the house next month. Scheduled next tune up d
Returned to add leak dye into upstairs/Masterbedroom system. Will return in 7days to perform search for leak with black light.
System- upstairs Approx Age of System: 5 Refrigerant Type- R410a Metering Device- TXV SP/HP: 118/285 SLT/LLT: 48/84 VSAT/LSAT- 38/92 Superheat/Subcool- 10/8 Outdoor Entering Air Temp-80 Outdoor Fan FLA- .5 Compressor RLA/LRA- 8.6/85 Contactor Voltage-242 Capacitor Rating- 45/5 Actual 44.7/5 Indoor Return Dry Bulb Temp-68 Return Wet Bulb Temp- 60 Supply Temp- 53 Temperature Difference-15 Required Difference-15 Blower FLA- 5.5 Filter Sizes â€“ 16x25x4 Changed Filters â€“ N Clean Blew out drain line: N no blow out valve Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes- system was operational upon arrival. Performed tune up and let customer know she does have a pan switch to detect the water but itâ€™s a last line of defense recommended in line switch to catch the water before it hits the pan and a blow out valve to keep primary line clear. Also recommended air scrubber to keep the upstairs air clean. Recommended adding the other
Came out today to perform a whole house inspection. Found a couple of minor issues in address them with customers. Save estimates for anything I found. Customer is going to go over everything with her son and go from there.
Arrived to check toilet leaking. Upon arrival customer had water off to toilet. Felt around tank and bowl, found water leaking from right tank bolt leaking onto the linoleum. Replaced tank to bowl kit and recaulked toilet. Customers will review comfort club pamphlet and think about it for a later time.