The Bradbury Family has been Serving Your Air Conditioning, Heating & Plumbing Needs for 30+ Years
Our family are experts to your family when it comes to Cooling, Heating & Plumbing for your home and business near Humble, TX. Our family gives you our personal promise that we won’t be happy until you’re 100% satisfied! Our reputation is based on your 100% satisfaction, and we take that promise seriously. It’s a part of our company mission!
Call us now at (281) 651-5484 or (936) 271-2030 for fast and friendly service. We’d love the opportunity to earn your business as we have with your Porter, TX neighbors.
See what your neighbors are saying about our services below!
for Humble, TX
Our Reviews by City
Dan - Humble, TX
Jeremy was excellent in helping my wife and I with our inspection. Definitely went above all expectations to make sure we understood the process and completed job and more in A+ fashion
Response from Bradbury Brothers Cooling, Heating, Plumbing & Electrical:
Thank you so much, Dan! Our goal is 100% satisfaction with our people, products, and services. We are so excited to hear that we received an A+ from you! Thank you for giving us the opportunity to serve you.
Water Heater Evaluation
Somerr - Humble, TX
Overall great service !
Carl - Humble, TX
Not completely satisfied with the small service fee that was charged because this was a follow up request for a previous call that was not resolved. Still, I highly recommend Bradbury Brothers and their service over the years have been excellent !!
Homeowner worried about water heater making popping noises when no water was being used. Shane was out last week and flushed out. Explain to homeowner that that is not a permanent fix and it might not work to keep the noise down. Also explain to homeowner the reason each came on we nobody was using the water because the temperature outside dropped the temperature in the tank low enough for the thermostat to kick it on. She understands now on way to meet noises without being used. Also noticed upstairs guest bathroom sink was really slow draining due to AC condensation. Gave estimate to snake out. Homeowner has scheduled for next Thursday to snake it out and do home inspection.
Check water heater in attic. Customer wanted heater flushed. Also noticed the heater was taller than the original and whoever put it in just pushed exces vent pipe out roof and did not lower the storm collar. Flushed water heater and cut down vent pipe where storm collar can do its job.
Need after hours plumbing services. Water leak in shower. Turn water off at the meter. Water is still leaking. Replace main water shut off valve. Repair water leak in shower. Water fixtures have hard water spots and scale build up. Recommend new Gemline water softener and KDC filter.
Heater making noises. Heating repair and maintenance tune up. Diagnose and perform annual heater maintenance service plan on York heating system. Replace capacitor and check furnace on 12 year old HVAC system. Heater maintenance complete which will help lower heating cost for this residential customer. R22 refrigerant will be phased out in January 2020. Recommend replacement with new Comfortmaker air conditioning system. Heating system is now ready for winter weather.
Heater not turning on. Heating repair and maintenance tune up. Diagnose and perform annual heater maintenance service plan on Daikin heating system. Add freon and check furnace on 10 year old HVAC system. Heater maintenance complete which will help lower heating cost for this residential customer. Filters are dirty. Filters should be changed monthly for best performance. Heating system is now ready for winter weather.
Hot water heater not making hot water. Diagnose and find water heater is over 8 years old and should be replaced. 8 year old Rheem water heater. Recommend replacement Rheem tank water heater, or Navien tankless water heater. Average water heater life span is 8-12 years old. Install new Navien tankless water heater with new pan and test for functionality. Recommend Gemline water softener to protect new water heater from hard water damage.
System: Downstairs Approx Age of System: 3 Combustible Gas Leak Detection Pipe and fittings leak-free: yes Valves and orifices leak-free: yes Carbon Monoxide Testing Walk-around CO: pass/ppm-0 Airside CO: pass/return ppm-0 supply ppm-0 Flue gas CO: pass/ppm-35 Ignition and Combustion Delayed ignition: no Flame disturbance: no Flame discoloration: no Motor Amperages and Capacitors Blower motor FLA: 5.6 Induced draft/combustion blower motor FLA: .6 Capacitor(s): pass Temperature Rise Rated: 25-55 Actual: 43 Static Pressures Blower speed/cfm: RP- .36 /FS- .22 /SP- .1 TESP: .58 Safety Controls Primary limit test: pass Filter sizes: 20x25x1 Changed filters: no. Itâ€™s clean. Scheduled next tune up date: Notes: ________________________________________ System: Upstairs Approx Age of System: 3 Combustible Gas Leak Detection Pipe and fittings leak-free: yes Valves and orifices leak-free: yes Carbon Monoxide Testing Walk-around CO: pass/ppm-0 Airside CO: pass/return ppm-0
Diagnostic System: Amana Refrigerant Type R410A Metering Device-TXV SP/HP 58/225 SLT/LLT 81/78 VSAT/LSAT 7.4/77 SH/SC 73/0 Outdoor Entering Air Temperature 75 Notes: Customer stated that her ac unit isnâ€™t cooling properly. On arrival checked tripped float switches and none found tripped, did find traces of water in the emergency drain pan. Then went to condenser and checked for normal operations and found condenser refrigerant charge was low. Spoke with customer about findings and did inform her that system has a possible leak, and until leak is repaired system is at high risk of refrigerant leaking out. Customer chose to add refrigerant at this time added 4lbs of 410-A to get unit back cooling and would like to have office check warranty and see what the next step would be. Added refrigerant and checked temperature split between return and supply, unit has 15 degree temperature split. Unit is cooling at this time. Recommendations:
Recommending navien tankless water heater and gemline water softener
Recommending navien tankless water heater and gemline water softener
Installed 12x12 return in master bedroom
Lennox ac tune up.
Diagnostic on Goodman system.
Diagnostic on Payne system.
Performing semiannual air conditioning maintenance tune-up on two Heil and Bryant AC systems for a residential Comfort Club member. Programming thermostat, checking air filters, testing safety controls/detectors, balancing airflow, assessing ductwork, taking vital readings, and evaluating HVAC system performance. Systems are cooling and ready for Summer weather.
Daikin ac tune up.
Bryant ac tune up
Fixing duct work!
Extending flue vent from install
Bryant furnace tune up.
Replace thermostat for heat pump system.
Lennox furnace control board replacement.
Troublehot a tankless water heater.
Goodman furnace tuneup.
Furnace diagnostic on Bryant system