Top Rated HVAC, Electrical & Plumbing Services in Montgomery County, TX
Our family are experts when it comes to Electrician, HVAC and Plumbing services for your homes and businesses. Our family gives you our personal promise that we won’t be happy until you’re 100% satisfied!
We take that promise seriously and it’s a part of our company mission!
HVAC Repair, Plumbers & Electrician FAQs
It costs around $350-$600 to repair an HVAC unit in Montgomery, TX. However, the cost can vary due to:
- The kind of HVAC repair.
- How extensive the HVAC repair is.
- The HVAC contractor’s hourly fee.
The following is included in a heating and air conditioning tune-up in Montgomery, TX:
- A cleaning of your heating and air conditioning system.
- An inspection of your heating and air conditioning system.
- A lubrication of your heating and air conditioning system’s moving parts.
- A replacement of your heating and air conditioning system’s air filter.
In some instances, a heating and air conditioning system tune-up may also include minor repairs, depending on your HVAC contractor. To find out more about getting your heating and air conditioning unit tuned up, contact us today.
An electrician usually charges around $8,000-$15,000 to rewire a house in Montgomery, TX. The cost can fluctuate depending on:
- The age of your home.
- The size of your home.
- The accessibility of your wiring.
Having your home rewired can be expensive, but very worthwhile since it will allow your electrical systems to operate more efficiently and will provide an added measure of safety. To get your house rewired, call us today.
Who do you call in Montgomery, TX if you have a broken pipe? That depends on the location of the pipe. If the broken section is past your property line into the street, it is the city’s responsibility. If it is underneath your property, you do need to call a plumber.
Remember that a broken pipe is an emergency! Along with property damage, you could also be responsible for a steep water bill if you wait too long to call for a repair. Bradbury Brothers can help. Call now if you have a major leak on your hands!
Zip Codes and Areas Served:
Call us now at (936) 271-2030 for fast and friendly service. We’d love the opportunity to earn your business as we have with your Montgomery, TX neighbors.
See what your neighbors are saying about our services below!
for Montgomery, TX
Our Reviews by City
Jyme - Montgomery, TX
New Home AC inspection
Johan - Montgomery, TX
Dependable and Consistent!
Angela - Montgomery, TX
Bradbury Brothers are legitimately the best! Shane showed up today prepared and solved our problem within an hour. He was kind, professional and thorough!
Christine - Montgomery, TX
Linda - Montgomery, TX
kind of high but Mike made it a little more palatable
Sims - Montgomery, TX
As always, Bradbury Brothers sent a professional technician out who took care of our issue quickly!
Chris - Montgomery, TX
Great service and on time.
Outstanding Service and Great Price
John - Montgomery, TX
Jim is very professional, friendly guy. Performed the work requested and did an outstanding job
Michael - Montgomery, TX
Explained things and fixed the problem.
Terry - Montgomery, TX
Great employee. Personable, knowledgeable and a nice man. He will be coming back to install the grab bars in my toilet. I am impressed with the employees that Bradberry has sent to our house.
William - Montgomery, TX
Michael - Montgomery, TX
Great and fast service
Susan - Montgomery, TX
Excellent service. Outstanding technician
Bob - Montgomery, TX
Frank - Montgomery, TX
Todd - Montgomery, TX
Good effort to repair problem... just to many failures (2 units 5 failures in 5 years)
Courtney - Montgomery, TX
Great Service & after hours response
BB - Montgomery, TX
Love that I get a call back late up to midnight & service scheduled promptly. Professional, knowledgeable and respectful, especially of covid distancing.
David - Montgomery, TX
David - Montgomery, TX
Great service and very thorough
Terry - Montgomery, TX
Explained in detail what needed to be done. Highly knowledgeable. Jason was very nice and friendly I would highly recommend Bradbury Brothers.
On time service, diagnosed quickly
Todd - Montgomery, TX
Good experience with professional technician
Sheila - Montgomery, TX
He couldn’t help us because blown compressor. Still very nice kind honest guy
Jon - Montgomery, TX
Henry did an excellent diagnosis and worked to ensure even though we need to order a part that we are running and the house is cool
Mike - Montgomery, TX
What can I say, Marc is great. Is thorough and experienced. He does a great job.
System-upstairs Approx Age of System: 5 Refrigerant Type- R410a Metering Device- TXV SP/HP:115/314 SLT/LLT:62/95 VSAT/LSAT- 39/98 Superheat/Subcool-23/3 Outdoor Entering Air Temp-88 Outdoor Fan FLA- .7 Compressor RLA/LRA-6.7/61 Contactor Voltage-243/27 Capacitor Rating-35/4 of 35/5 Indoor Return Dry Bulb Temp-75 Return Wet Bulb Temp-65 Supply Temp- 60 Temperature Difference-15 Required Difference-16/24 Blower FLA- 1 Filter Sizes â€“ 14x20 16x25 Changed Filters â€“ N Clean Blew out drain line: N Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes-organic growth found in supply plenum and air handler, recommend an air scrubber to kill off organic growth, prevent further buildup as well as increase air quality, recommend a sanuvox uv surface light to kill off organic growth inside of system , help prevent further buildup, and help keep inside of system clean. Recommended blowout valve for both systems to allow drain line to be cleare
Return to replace ductwork Arrived on site, met with Mr Brown. Disconnected and removed old flex duct. Installed new flex to both connections underneath the home, and disposed of old flex. We do offer a Platinum Comfort Club Membership Our HVAC Comfort Club Membership is $13.95 per month per system or $167.40 yearly Benefits: Guaranteed service within 24hrs Discounted Service Charge $49 (Regular $98 afterhours $148) 20% discount on repairs Semi- Annual HVAC System Tune Ups (2 per year Cooling/Heating) Please feel free to contact our office if you would like to proceed with any of the recommendations or have any questions. Non Comfort Club $1710 Comfort Club $1368
Approx Age of System: Main 7 Refrigerant Type-R410a Metering Device- TXV SP/HP: 134/305 SLT/LLT: 71/97 VSAT/LSAT- 47/96 Superheat/Subcool- 21/5 Outdoor Entering Air Temp- 83 Outdoor Fan FLA- 1.25 Compressor RLA/LRA- 11.39/124 Contactor Voltage- 242/24 Capacitor Rating- 46/8 Indoor Return Dry Bulb Temp- 76 Return Wet Bulb Temp- 66 Supply Temp- 60 Temperature Difference- 17 Required Difference- 15-20 Blower FLA- 6.95 Filter Sizes â€“ 20x25x4 Changed Filters â€“ Clean Blew out drain line: Y Returned tstat to original settings: Y Unit operational; prior to leaving: Y Approx Age of System: master 7 Refrigerant Type- R410a Metering Device- TXV SP/HP: 133.5/336 SLT/LLT: 64/93.9 VSAT/LSAT- 46.5/103.8 Superheat/Subcool- 18/10 Outdoor Entering Air Temp- 83 Outdoor Fan FLA- .83 Compressor RLA/LRA- 6.17/83 Contactor Voltage- 240/25 Capacitor Rating-47/6.2 Indoor Return Dry Bulb Temp- 73 Return Wet Bulb Temp- 63 Supply Temp- 55 Temperature Difference- 18 Requir
Arrived on site and met with customer went to attic and inspected ductwork and HVAC unit. Found water in the emergency drain pan coil and supply Plenum were sweating. Got static pressures total external static pressure is .76, ductwork is undersized causing high static pressure. Checked drain line outside water is in the pan water is not draining all the water out of the pan, the pitch needs fixed.
Arrived to the Essex residence to do a whole house electrical inspection. At the time of the inspection everything seem to be safe and in good working order. At this time I do not see a reason to do a follow up call.
As Per Agreement
Arrived on site met with customer went to attic found system was clogged checked sink it was plugged as well. customer unclogged sink I installed a pan safety switch and blowout valve, cleared the primary drain line and emergency drain line.
System- upstairs Approx Age of System: 4 months Refrigerant Type- R410a Metering Device- TXV SP/HP 139/344 SLT/LLT: 59/97 VSAT/LSAT- 48/105 Superheat/Subcool- 11/8 Outdoor Entering Air Temp-94 Outdoor Fan FLA- .6 Compressor RLA/LRA-6.4/46 Contactor Voltage-245 Capacitor Rating- 35/5 actual 35/5 Indoor Return Dry Bulb Temp-80 Return Wet Bulb Temp- 72 Supply Temp- 59 Temperature Difference-21 Required Difference-15-20 Blower FLA- 1 Filter Sizes â€“ 20x20x1 Changed Filters â€“ Y customer provided Blew out drain line: Y Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes- system was operational upon arrival. Performed tune up on new Bradbury installed unit and unit is operating within manufactured specs specs at this time. Scheduled next tune up date: Jan 6 12-4
PSI - 152/444 SAT - 53/125 SHSC - 10/29 LT 63/96 80r - 65s = 15*td 71*wb = 14* target System is overcharged. Overcharge conditions will often result in increased humidity in the areas controlled by the affected unit. Mr. Bass opted to leave conditions as they are and seek to follow up with the last company to work on the system.
We came out today to look at the customers water heater. We gave pricing on changing the gas control since it wouldnâ€™t Light or changing it out for a new rheem. The customer went with a new heater and we got it changed out in a timely manner. The customer now has hot water again and is pleased with the service. Also is signed up for comfort club again and would like it 5 months out same time of day with a warning call.