5 Star Rated Plumbing & Air Conditioning Services
Family matters. For more than 30 years the Bradbury Family has been providing local air conditioning and heating home comfort service solutions in The Woodlands with 100% Satisfaction Guarantees! It’s part of our company mission. We’ve also been named Best of the Woodlands HVAC Contractor for 7 consecutive years!
Top Rated Plumbers in The Woodlands
Due to overwhelming demand, Bradbury Brothers began providing plumbing services and local Plumbers in The Woodlands, TX to satisfy the needs of our residents for highly qualified and well-trained plumbers.
See what your Woodlands neighbors are saying about our services below!
for The Woodlands, TX
Our Reviews by City
Excellent service, great price.
Liz - The Woodlands, TX
Bradbury and my tech Jason are great. I had a simple drainage issue Jason assessed the problem and fixed the problem quickly. I couldn’t be happier. Great experience. Thank you!
John - The Woodlands, TX
Jeremy was professional, knowledge, and efficient. Overall, top quality guy.
Sergio - The Woodlands, TX
Pat - The Woodlands, TX
Great Service, fast and efficient
Roger - The Woodlands, TX
The Plumbing repairman arrived at the time scheduled, and promptly diagnosed the problem with our leaking sink. The repairman inspected all the sink drain pipe and fittings and the water supply valves and faucet connections. He quickly made the repair and then carefully checked the sink to ensure there was no further leakage.
Francisco - The Woodlands, TX
They pretend to be profesional and honest but they are a big disappointment. I call to request an AC filter change. As simple as that. First they came and told me they did not stock filters then send me the info on the filter so I could order it myself. They told me they will come back and change it for free, they did try to charge but finally they did not, the problem is that they email me the wrong filter spec. I need to return the first one I order, order the new one and they will kindly come back for a 98 dollars fee.
Michael - The Woodlands, TX
Excellent fast service
Cindy - The Woodlands, TX
Both air and plumbing services were professional and efficient with great communication.
Replace bathroom sink valves; replace gas supply line for water heater
Don - The Woodlands, TX
Cindy - The Woodlands, TX
Caleb was very professional. He was respectful and educated and helped us with all our concerns
Return to install blower motor and capacitor and check for proper operations. 69/242 psi 38/114 sat 93/110 lt 55/4. Shsc Oat 93 88 inside - high heat load. System operational.
System- Upstairs Approx Age of System: 4yrs Refrigerant Type- R410a Metering Device- TXV SP/HP: 130/337 SLT/LLT: 53/98 VSAT/LSAT- 43/104 Superheat/Subcool- 11/5 Outdoor Entering Air Temp- 94 Outdoor Fan FLA- 1.1 Compressor RLA/LRA- 14.0/*** Contactor Voltage- Capacitor Rating- 28.78/4.91 Indoor Return Dry Bulb Temp- 73 Return Wet Bulb Temp- 57 Supply Temp- 55 Temperature Difference- 18 Required Difference- 16-20 Filter Sizes â€“ (2) 20x25x4 Changed Filters â€“ Y (customer supplied) Blew out drain line: Y Returned tstat to orig in al settings: Y Unit operational; prior to leaving: Y Notes- Unit was operational on arrival. Checked filters. Checked operating pressures and temperatures. Checked indoor and outdoor electrical. All other components showed no visible issues at this time. Recommend condenser coil cleaning-( to reduce amp draw and increase efficiency) and surge protector-(to protect equipment from brown outs and power surges). System- Downstairs
AC Diagnostic System: Workshop. PTAC unit Refrigerant Type R410A Metering Device-TXV SP/HP na SLT/LLT Na VSAT/LSAT na SH/SC na No service valves Outdoor Entering Air Temperature 94 Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes: Arrived on site met with customer. Went to workshop to see unit. Found that it was a PTAC unit and was not draining properly. Customer requested a small hole to be drilled in pan to allow drainage to ground. (Due to no drain hole from the factory or original installation.) Per customer request knowing Bradbury Brothers has no liability for any issues from hole put into casing and pan. A hole was made to allow drain. A 1/4â€ hole was drilled into pan to allow drainage of pan. System is operational. Recommendations:
AC Diagnostic System: Casita Refrigerant Type R410A Metering Device- TXV SP/HP 133/324 SLT/LLT 57/91 VSAT/LSAT 46/101 SH/SC 11/10 Outdoor Entering Air Temperature 91 Filter Size(s) 20x25x1 Notes: Leak was found during tune up. I returned pumped down the system then cut back the insulation on the suction line in the attic and found multiple leaks in a 7 foot section. Cut out the whole 7 foot section and replaced with new copper pipe and tubing insulation. Pressurized the system with nitrogen to 400 psi and let stand for 10 minutes. Pressure held indicating no more leaks. Pulled vacuum to 500 microns and released the refrigerant and added 2 pounds to replace what was lost. System is operating within manufacturers specifications at this time. Called home owner and left voicemail on completion of the job.
Service Customer has a TSTAT upstairs that needs changed out. Replaced thermostat. Checked for operation. No issue. Mr. Clayton has no cooling complaints and thermostat was satisfied on arrival.
Diagnostic Poor cool in living room. Found blower wheel very dirty. - this can reduce the flow of air through the ductwork. Found condenser coil extremely dirty. - this causes the condenser to run hot because the proper amount of heat cannot be rejected at the condenser preventing the indoor air from being as cool as it should. This will help to cool the apartment but I cannot guarantee it will be the only steps needed. Recommendations and todayâ€™s cost approved via phone.
Came out and made some minor adjustments to the customers shower, customers happy no charge for the call.
Arrived to the Tienhaara residence to complete the estimate that she approved. When I was done I checked to make sure everything that I installed was working properly. At this time as you no reason to do a follow call.
System-casita Approx Age of System: 1 year Refrigerant Type- R410a Metering Device- TXV SP/HP: SLT/LLT: VSAT/LSAT- Superheat/Subcool- Outdoor Entering Air Temp- Outdoor Fan FLA- Compressor RLA/LRA- Contactor Voltage- Capacitor Rating- Indoor Return Dry Bulb Temp-76 Return Wet Bulb Temp-63 Supply Temp- 56 Temperature Difference-20 Required Difference-16-24 Blower FLA- 2.5 Filter Sizes â€“ 20x25x4 Changed Filters â€“ Y truck stock, customer paid for. Blew out drain line: N Returned tstat to original settings: Y Unit operational; prior to leaving: LEAK DETECTED Notes-leak detected in the attic coming from suction line. Oil on attic floor as well as coming from the rubatex. Did not perform tuneup because of this. Customer will be notified when we have an available tech to perform the repair. Also changed other 2 systems filters, both 20x25x4, had spares in attic for the 2 systems. Scheduled next tune up date: Tuesday December 22 , 10-2
AC Diagnostic System: Main Refrigerant Type R410A Metering Device- TXV SP/HP 121/291 SLT/LLT 55/89 VSAT/LSAT 41/93 SH/SC 13/4.5 Outdoor Entering Air Temperature 87 Filter Size(s) 20x25x4 Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes: The Browns have a one zoned system for the house. The master bedroom is not cooling the rest of the house is properly cooling. Turned on the system and checked the zone dampers. The damper that supplies the master failed and is stuck closed. Replaced failed Damper motor then cycled zones to make sure new and old dampers were all working properly.
System- 1 Approx Age of System: 1yr Refrigerant Type- R410a Metering Device- TXV SP/HP: 124/302 SLT/LLT: 58/91 VSAT/LSAT- 42.7/96.6 Superheat/Subcool- 15/5.5 Outdoor Entering Air Temp- 81 Outdoor Fan FLA- 1.08 Compressor RLA/LRA- 11.20/98 Contactor Voltage- 240/24 Capacitor Rating- 45/7.4 Indoor Return Dry Bulb Temp- 71 Return Wet Bulb Temp- 61 Supply Temp- 54 Temperature Difference- Required Difference- 15-20 Blower FLA- 8.80 Filter Sizes â€“ 20x25x4 Changed Filters â€“ N (dirty customer will replace) Blew out drain line: Y Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes-Performed ac tune up x1, furnace is about 1 month old, rest of system is about 1yr old. Indoor unit is working properly, did find media filter really dirty which will cause restriction of airflow and cooling issues. informed customer, will recommend box of 6. Checked outdoor unit found unit working properly with no issues, recommended box of 6, spoke wit
Came out today to install customer supplied shower trim and slide bar, and flush customers tankless water heater. After a few snags the shower is complete, not leaking anymore and the tankless is flushed. Customer paid with check by capture and no follow up today.
Arrive to the Baker residence to go over the list of items he would like done. I presented the estimates which he approved and it is scheduled for this Sunday.
Arrived to the Lamoine residence to install the generator plug on the side of the house. I also installed the interlocking main breaker device so that he could run the generator safely. While I was there he mentioned he was having problems on the second floor with the breaker not operating properly. After doing the troubleshooting I came across multiple wires that have been nicked or cut that were touching other wires in the boxes. At this time everything seems to be safe and in good working condition. I do not see a reason to do a follow up call.
Pulled toilet tank and installed new tank to bowl kit. Set tank back and filled with water . Tested for leaks and found none. They let me know the shower upstairs has a small drip continually coming out. Need to get approval to replace shower cartridge .
Diagnostic Single System Blower motor failed. Skyler scheduled for this evening. Price out blower motor and follow up - furnace info attached 20uf run cap with blower.
Diagnostic Upstairs unit. Found inline float triggered. Bathroom sink is clogged and not draining. Sink will need to be addressed before the drain line is cleared. Mr. Vedala will address sink issue.
After a Seiter couldnâ€™t stop the condensation line we came out and ran hand rod through it until it went through the inch and a half P-trap. Also poured some bio one down there too sure the customer has the AC up and running, no charge for the call customer already paid the AC tech and no follow up.
System analysis x1 Closet unit over flowing over internal drain pan and coming out of a register in the kitchen. Attempted to blow out drain and was unsuccessful, scheduled to have a plumber come out and clear line. Issue happens every year and usually blowing it out works but not this time. Plumber is scheduled and will arrive tonight.
We were out today to do our annual home inspection. In the upstairs hall bath, found the chain for the flapper disconnected from the handle. Reconnected the chain and toilet is working as it should. Besides this issue everything seems to be working as it should. There is no follow up.
System- U/s Approx Age of System: 3 Refrigerant Type- R410a Metering Device- TXV SP/HP: 121.5/301.2 SLT/LLT: 49.7/89.5 VSAT/LSAT- 41.3 Superheat/Subcool- 8.4/6.5 Outdoor Entering Air Temp- 82 Outdoor Fan FLA- .4 Compressor RLA/LRA- 8.1/82.6 (High energy draws on start up) Contactor Voltage- 244 Capacitor Rating- 44/3 Indoor Return Dry Bulb Temp- 74.5 Return Wet Bulb Temp- 46.2 Supply Temp- 54.7 Temperature Difference- 20 Required Difference- 16-20 Blower FLA- 3.8 Filter Sizes â€“ 16x25x1/12x12x1/12x24x1 Changed Filters â€“ N (customer will replace at later time) Blew out drain line: Y Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes-high energy draws on start up, UV bulbs burned out, attic access needs to be insulated. Scheduled next tune up date: would like follow up closer to the fall season to schedule next tune up. System-D/s Approx Age of System: 3 Refrigerant Type- R410a Metering Device- TXV SP/HP: 115.3/292.
Arrived to the Tienhaara property to look at some electrical issues. . Entry chandelier has bulbs not working ( recommend replacing with LED bulbs ) . Doorbell was functioning while I was there ( donâ€™t see an issue ) . The garage light needs a new ballast. Recommend bypassing ballast and installing LED bulbs instead for efficiency and longevity . One under counter light in the kitchen is not functioning properly ( might need a new ballast ). Recommend bypassing the ballast and installing an L.E.D. under cabinet light. . The fireplace in the living room has power and I believe itâ€™s controlled by a switch on the left-hand side next to the bookcase. ( recommend getting someone out there familiar with fireplaces to check the gas and to make sure the flute is clean before operating )
Homeowner had to back out today to install delta handle and wand that delta sent for warranty replacement. Everything is working properly.
Tank to bowl is leaking and needs to be fixed. Have to wait for approval from owner to proceed going to send estimate over. Sent e mail over for approval .
System-downstairs daikin Approx Age of System: Refrigerant Type- R410a Metering Device- TXV SP/HP:113.8/252.8 SLT/LLT:67.7/72.7 VSAT/LSAT- 37.8/84.3 Superheat/Subcool-27.3/8.8 Outdoor Entering Air Temp-72 Outdoor Fan FLA- 1.1 Compressor RLA/LRA-13.3/165.8 Contactor Voltage-244.6/25.3 Capacitor Rating-68.5/4.95 Indoor Return Dry Bulb Temp-72.5 Return Wet Bulb Temp-63.4 Supply Temp- 48 Temperature Difference-24 Required Difference-16-22 Blower FLA- 6.9 Filter Sizes â€“ 20x25x1/12x12x1/20x25x1 Changed Filters â€“ N (customer will change out) Blew out drain line: Y Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes- Scheduled next tune up date: System- Approx Age of System: upstairs Refrigerant Type- R410a Metering Device- TXV SP/HP:139.6/260.8 SLT/LLT:61.2/79.6 VSAT/LSAT- 48.4/86.4 Superheat/Subcool-12.7/6.7 Outdoor Entering Air Temp-72 Outdoor Fan FLA- .6 Compressor RLA/LRA-5.4/71.3 Contactor Voltage-243.9/2
Home owner had hole cut where leak was. Manifold tee for bathroom had leak. Had to cut out the manifold and install new one. Installed and checked for leaks and found none
We came out today to see about changing the master shower valve out for the customer, but the customer was disappointed with the valve and trim that he had purchased from Home Depot so we gave him a better option which is rebuilding the valve thatâ€™s in the wall to avoid from cutting a hole in the master bedroom and upgrading it to his liking. Also adjusted the handles to the lavatory in the powder bath to get it to stop dripping, and as a courtesy check the water heater which we noticed it was a tankless and had never been flushed before so we did give him an estimate to do that when we come back and do the master shower. Customer has everything he needs ordered and will be here by Monday from Amazon so our appointment is set for Tuesday to complete the work. Customer also signed up for comfort club and has paid the yearly fee and we have the first appointment for the annual plumbing home inspection Scheduled for September 10 from eight to 2. Customer paid with check , And we will be
Checked faucets upstairs and found angle stops off. Turned on and Checked for leaks and found none. In tub the drain had plastic blocking it just pulled out and it was draining good. Soap tested stove and found no leaks . He said the burners were all not working and let him know it would be a appliance guy that would need to check them gas up to it is good and has no leaks .