The Bradbury Family has been providing Air Conditioning, Heating & Plumbing Needs for Tomball, TX residents for 30+ Years
Our family are experts when it comes to heating and cooling your homes and businesses. Our family gives you our personal promise that we won’t be happy until you’re 100% satisfied! Our reputation is based on your 100% satisfaction, and we take that promise seriously. It’s a part of our company mission!
Call us now at (281) 651-5484 or (936) 271-2030 for fast and friendly service. We’d love the opportunity to earn your business as we have with your Tomball, TX neighbors.
See what your neighbors are saying about our services below!
for Tomball, TX
Our Reviews by City
Great service as always!!
Deborah - Tomball, TX
The technician was on time, friendly, efficient and did the work correctly. He’s also a Marine so he knows how to work.
Joy - Tomball, TX
Caleb was wonderful! Very professional and very kind. Even returned the next day to check on the job and help out more at no additional charge. I’ll use Bradbury Brothers for plumbing repairs every time.
Commerical AC repair
Fielding's - Tomball, TX
On time, very professional, fixed the problem
Jason - Tomball, TX
Excellent service. Very professional.
Great Inspection and Investment!
Jacob - Tomball, TX
Shane and Charles preformed a plumbing inspection for our home recently and it was very informative. We had a few plumbing issues initially in our home and they spotted them along with other issues that we needed to fix. Overall very happy with thier service and inspection.
Ryan - Tomball, TX
Maria - Tomball, TX
Juan Martinez has been to our house for other appointments and he is friendly and good at his job.
Sandy - Tomball, TX
Jamie - Tomball, TX
Fernando is the best.
Called before i even knew my A/C was down.
Matt - Tomball, TX
I was out working on my yard and got a call from the office saying the condenser was not communicating anymore with the thermostat and was asked if all was ok. Went inside and found the A/C not working anymore. Love the smart system that emails the office when there is a problem. Tech was able to come out and diagnose the problem. Got parts the next day and was up and running again.
Dale - Tomball, TX
Called Bradbury Brothers when my A/C stopped working around 1pm. Of course, it had to be a Saturday when we'd invited friends over for dinner and had family from out of town staying with us. They had a technician at our house by 4pm and the problem soved shortly thereafter. Ronald, the technician was nice, polite and quickly identified and resolved the problem. Couldn't have asked for more!
Nicole - Tomball, TX
Arrived in time window allotted, very knowledgeable, great service.
Frank - Tomball, TX
Bruce - Tomball, TX
Another great job by Jim & Bradbury Brothers.
Excellent Service as Always
Lance - Tomball, TX
Jim and his team showed up on time and completed our project in a very reasonable time. Everything we wanted is done and working 100% perfectly.
Jeremy did a great job! He’s very thorough and polite!
Katie - Tomball, TX
Convenient and safe
John - Tomball, TX
Sandy - Tomball, TX
Caleb was awesome! A bit pricey but it was on Sunday so after hours applied. You can’t plan for a pipe burst so gotta pay to get water back on. Was appreciative they got to me within 4 hours of calling and technician was super knowledgeable, friendly and respectful. Would use them again in future.
Rosemarie - Tomball, TX
Good price great service
Jenna - Tomball, TX
Mario was professional and on time.
Excellent Service as Always
Lance - Tomball, TX
We always receive excellent and on time service from Bradbury Brothers
Eva - Tomball, TX
Bruce - Tomball, TX
I've dealt with Jim before. Always a great experience.
He was great
Linsey - Tomball, TX
Great follow up service-Juan
Vic - Tomball, TX
Juan Parra/ Installation manager/ followed up to check on a couple of issues with our install of 3 systems. One issue was found quickly in a noise was the return air register which was fixed quickly, The other was resolved by adjusting the duct dampers for air flow. Thank you Bradbury Team!
Came out today and put the top back on the Faucet in the guest bathroom. Ran it and tested it as much as possible to ensure no leaks and we also moved it as forward as we could so she could get her hands down comfortably in the sink. Customer paid with credit card the service fee and no follow-up needed.
As Per Agreement
Returned to install 2 media cabinets with plenum. Rebuilt flue vent to avoid making contact with secondary return plenum. Checked for proper operations, removed all 1in filters from wall. Showed customer repair. Made sure unit was completely operational before departure.
Home owner had a leak in wall. Repaired leak. Also wanted a price on installing a ice maker in washer area. Sending bid for ice maker and repaired leak in wall and turned water on to check for leaks. Found none
System- Single Approx Age of System: 1 Refrigerant Type- R410a Metering Device- TXV SP/HP: 109/307 SLT/LLT: 48/83 VSAT/LSAT- 36/97 Superheat/Subcool- 12/13 Outdoor Entering Air Temp- 81 Outdoor Fan FLA- 0.9 Compressor RLA/LRA- 8.4/76.1 Contactor Voltage- 244 Capacitor Rating- 40/5 Indoor Return Dry Bulb Temp- 71 Return Wet Bulb Temp- 58 Supply Temp- 50 Temperature Difference-20 Required Difference- 20 Blower FLA- 4.1 Filter Sizes â€“ 12x12 (2), 12x20 Changed Filters â€“ N Blew out drain line: Y Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes- performed ac tuneup. System was operational upon arrival. Angel expressed interest in the air scrubber but does not want to do it on this visit. Scheduled next tune up date: 01/14
Customer had us out today for a dripping faucet in the mast bath. Replaced the cartridge in the lav on the right hand side. Turned water on and checked for leaks and functionality, everything is working as it should. Customer also had concerns about water c9ming from the dishwasher air gap. Removed hose from air gap and found a blockage. Cleared the blockag3 and everything is working as it should. No warranty on drain cleaning. We will need to schedule the QAC
System- upstairs Approx Age of System: 15 Refrigerant Type- R22 / Metering Device- Fixed Orifice / SP/HP: 61/175 SLT/LLT: 61/89 VSAT/LSAT- 35/92 Superheat/Subcool- 25/2 Outdoor Entering Air Temp- Outdoor Fan FLA- .7 Compressor RLA/LRA- 6.7 Contactor Voltage- 244 Capacitor Rating- Turbo Indoor Return Dry Bulb Temp - 74 Return Wet Bulb Temp- 66 Supply Temp- 55 Temperature Difference- 19 Required Difference- 15-20 Blower FLA- 3.7 Filter Sizes â€“ 20x25x1 Changed Filters â€“ N customer will Blew out drain line: N no blow out Returned tstat to original settings: Y Unit operational; prior to leaving: Y with issues Notes- Scheduled next tune up date: System- downstairs Approx Age of System: 1 Refrigerant Type- R410a Metering Device- TXV SP/HP:116/303 SLT/LLT: 54/77 VSAT/LSAT- 40/96 Superheat/Subcool- 15/18 Outdoor Entering Air Temp- Outdoor Fan FLA- .3 Compressor RLA/LRA-5.7/62 Contactor Voltage-243 Capacitor Rating- 40/5 Actual 40/5 Indoor
As Per Agreement
Came out today to give an estimate to run a drain line for the customers RV. The customer may end up digging the ditch lines for us to save money but we will need to provide an estimate to drop a pump grinding station and a stub out and run 2 inch line all the way down to the septic tank that is 125 feet away. The customer will be sending us pictures of where the tank is actually located and any other information that you can give us. We will be working on different estimates but for now the customer paid with credit card and we will follow up shortly.
Arrived on site met with customer, turn system on attached gauges outside and found system to be low on charge. Removed cover from air handler and found some ice on the coil. Scheduled a comfort adviser for tomorrow July 29 9-10a. Static pressures R .04 S .66. Advised customer to leave system off to have air circulation in the home. Left Comfort club brochure with customer
Arrived to check 5 year old disposal not working with switch. Reset is not tripped and disposal is not locked up. Unplug from wall and put in bottom outlet and it is now working, plugged back into the top outlet and it is now working, informed customer it could be the switch is getting weak. Disposal is in good shape and working properly at this time.
System- Downstairs Approx Age of System: 17 Refrigerant Type- R22 Metering Device- TXV SP/HP: 66/190 SLT/LLT: 68/94 VSAT/LSAT- 38/97 Superheat/Subcool- 29/3 Outdoor Entering Air Temp- 86 Outdoor Fan FLA- 1.36 Compressor RLA/LRA- 11/95 Contactor Voltage- 239 Capacitor Rating- 59.3/7.3 of 60/7.3 Indoor Return Dry Bulb Temp- 70 Return Wet Bulb Temp- 63 Supply Temp- 48 Temperature Difference- 22 Required Difference- 15-22 Blower FLA- 5.8 Filter Sizes â€“ 16x25x1 Changed Filters â€“ N Blew out drain line: Y Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes- Performed AC tune up. This drain line for this system is tied together with the upstairs and was backed up. I cleared the drain lines as included with the tune up. Recommend installing safety switches to prevent water damage to the house from future issues with the drain line. Systems are older and showing heavy fatigue, may require replacement soon, at this time they are still
Found refrigerant leak in the evaporator coil. The house is sold with closing on Friday. I have a comfort advisor scheduled for this afternoon between 1-2 for pricing on evaporator coil change out. Statics R-0.21 FR-0.54 FS-0.31 SP-0.15
System- Single Approx Age of System: 14 Refrigerant Type- R22 Metering Device- TXV SP/HP: 68/196 SLT/LLT: 52/96 VSAT/LSAT- 39/99 Superheat/Subcool- 13/3 Outdoor Entering Air Temp- 86 Outdoor Fan FLA- 1.2 Compressor RLA/LRA- 9.2/89.1 Contactor Voltage- 242 Capacitor Rating-60/10 Indoor Return Dry Bulb Temp-72 Return Wet Bulb Temp- 55 Supply Temp- 49 Temperature Difference- 23 Required Difference-21 Blower FLA- 6.8 Filter Sizes â€“ 20x30x1 Changed Filters â€“ N (clean) Blew out drain line: Y Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes- performed ac tuneup. System was operational upon arrival. System operating good at this time. Hardstart kit installed, run capacitor is a new turbo200X. Blowout valve and emergency pan switch installed. Recommended installation of an in-line float switch.